Psychrometric calculation (Mixture of air) - by-pass Factor - Humidification by steam - Adiabatic, temperature of saturation - Wet bulb temperature (BHS) - Flow condensates - transfer energy in the coil.
French site
| Home | Thematic | Tables | Programs | Library | Download | Links | Contact | Forum |
 _You are in the heading
--

PsychroSI program (mixed air calculation)
 Programs DevExcel DevExcel ? Estimate calculation Estimate (next) Synthesis, Graphic Library Help PsychroSI Psychrometric calculation Swimming pool Mixed air calculation AeroDuct Duct sizing Pressure loss coefficients Fan HydroTherm HydroWater Pipes sizing ThermExcel Pipes sizing HydroWater Local pressure loss Control valve Pump Orifice plate Expansion ThermoVapor Pipes sizing Local pressure loss Control valve Orifice plate Functions AeroGaz ThermGaz Aerogaz program Thermgaz program Local pressure loss Control valve Orifice plate Sundry programs AutoPlanning TriFile

Psychrometric calculation in air mixture with reheating

Simple reheating applies to the majority of the generators of heat used for the control of the temperature in the buildings.

The dry temperature increases, the temperature of dew and thus specific moisture remains constant.

The program can be used to carry out calculations in any new air, it will simply be enough nothing to input in the column B.

Heating of a room

Input the temperature of the room in winter in the case of a ambient heating. The thermal power of the coil must compensate for the losses of the room and the reheating of the new air at the ambient temperature.

 The simple reheating of the air of A to B can be represented according to the following diagram: The dry temperature (t) increases. The dew temperature (tr) and thus specific moisture remain constant. The rate of hygroscopic at contrary decreases. The wet temperature (th) increases.

Vapor humidifier: Evolution in the diagram of the humid air

The dry air (1) at the entry of the humidifier follows an evolution at constant temperature to be found at the exit as in point (2)

Actually, a very light heating exists, but negligible in practice thus ignored in the study.

Psychrometric calculation in mixture of air with cooling

In the majority of the applications of air conditioning, the air is partially dehumidified during the cooling of the air in the battery.

• Point A = State of the air at the air intake in the battery (Dry temperature and moisture)
• Point B = State of the air at the exit of air in the battery (Cooling and dehumidification)
• Point B1 = State of the air at the exit of air in the battery (cooling with constant specific moisture).
• Point C = outside temperature of wall (Tp) of the cooling coil. This temperature is calculated by the following empirical formula by considering that this temperature is not uniform of a point to another of this surface:
 th = Wet temperature T E_eau = Temperature of entered of water at the coil

program, software, softwares, computation, calculation, calculations, equations, psychrometric, air, by-pass, density, factor,
heat, enthalpy, humidification, vapour, dewpoint, moisture, content, dew, humidifier, adiabatic, relative, humidity, saturation,
temperature, wet, bulb, BHS, condensates, flow, transfer, energy, volume, dehumidification, cooling, conditionning, coil, coils,
battery

Last update:

Copyright © 2003-2014 - ThermExcel - All Rights Reserved